I have installed shortest wiring, and no overlap to avoid a crosstalk, and just put one Ferrite core to filter a common mode for wire organizing and 10cm overcome earth wires. It may affect on the high frequency, but, it is not our concern because LCF is for 110kHz L-to-L PLC & Noise filtering now.
Let me check what will happening,
Updated on NOV 29 2021
Long story is short, It is not working
This is an error what I do not want to get..
I have requested some advice and, Enphase said
Avoid a magnetic PLC coupling by
- Own enclouser :: it is related with a distance, but, -.-a
- 12" distance between conductor :: point to point is not important, parallel run is the key
Anyway, I have installed as
If I add an enclouser for the filter, I have to get a permit & inspection from local office. it become so complicated issue. and, I feel, so strange, the engineer do not understand what is the real problem.
anyway, I am not sure what is the cause why it can not block the signal from my next door,
i understand as it is a customized part for IQ. Maybe it is just a issue of my part.
while low current, Enovy is detecting the other enovy at outside.
IT is happening because my house has very quite in electric noise.
if not cut-out completely, the filter is not enough because still high SNR.