1. Will getting worse
2. Not related with GRID - no need to check grid or profile
3. Just power on reset - at first power on reset, it is showing 'Grid Instability Error' because no grid profile
I have requested a detail information abut LCF-064-1P,
Enphase - datasheet only
Manufacturer - can not provide it because customized item
No more solution with LCF, I have decided to return the filter on Enphase,
I am not sure the part is no good, or filtering is not enough.
So, I start to find the solution on my way,
I have reinstalled RP230-30-10-S and GTX-2300
BUT, it has too high line loss, so, I have disassembled & checked GTX-2300.
the coil configuration is the two-in-hand winding, it is good for common mode filtering, But, it has lower magnetic
leakage, so,not good for differential mode filtering. it is not much useful for me.
so, I have removed it. and, reduce 0.5mA leakage current & 10mOhm Resistance Loss
RP230-30-10-S have 60dB 50/50 insertion loss, but, can not block
the signal from next door also, I guess, my noise level at my home is too quiet and no one use PLC devices.
Yes, high SNR, so, just Envoy signal can be detected too easily.
so, I have decided to add an extra differential mode filter using ferrite
Ferrite core is B64290L0082X065
and, look the wire direction, it is the coupled differential mode, and 2 turns.
over one day, it can isolated successfuly, the expected core loss is 200-300Wh per year.
it is much less than 1~2kWh in GTX-2300-Y02.
This configuration will be saturated under 10A. so, I have tried on single turn.
at least, I need 20A because higher current will act as a noise, and will reduce the sensitivity of enovy.
and, I just need this inductor is working at the lower current (quite) zone.
This is final configuration.
It is working well, now, my system has been isolated completely.
and, no more cross-domain-traffic issue.
The cost of Ferrite & RP230 filter is just $80, and under $100 include tax & shipping.
It will working when system current is under 24A (around 20, IQ7+),
If want to apply on the bigger system, need bigger filter
This is an error what I do not want to get..
I have requested some advice and, Enphase said
Avoid a magnetic PLC coupling by
- Own enclouser :: it is related with a distance, but, -.-a
- 12" distance between conductor :: point to point is not important, parallel run is the key
Anyway, I have installed as
If I add an enclouser for the filter, I have to get a permit & inspection from local office. it become so complicated issue. and, I feel, so strange, the engineer do not understand what is the real problem.
anyway, I am not sure what is the cause why it can not block the signal from my next door,
i understand as it is a customized part for IQ. Maybe it is just a issue of my part.
while low current, Enovy is detecting the other enovy at outside.
IT is happening because my house has very quite in electric noise.
if not cut-out completely, the filter is not enough because still high SNR.
Very good video what is difference between Mico and String Inverters
You have to watch it before install a solar system.
Enphase MI system is much expensive than String inverter,
even more than Optimizer system.
But, String inverter system need 6+ panels in series, it means there is a minimum number of panels under similar sun-light condition. but, MI system do not have the minimum requirments, technically 1 panel.
so, if have small zone & multi zones (more than 2), MI should be better
except this condition, There is no advantage via the extra cost
We knew Enphase Envoy and Inverters are communicating using Power Line Carrier,
The Envoy IQ is using Line-to-Line Singal instead Envoy-S's Line-to-N/G Signal.
It is a huge difference, because Envoy IQ is generating Differential mode signal
and, OLD Envoy is generating Common mode signal
To filter the signal from my neighborhood (he has installed Solar System last summer, unfotunately, he & I under the same utility tranformer). To solve the cross domain traffic issue, I need to filter the differential mode signal.
I have installed RP230-30-10-S between IQ combiner busbar And Wire_to_load_center.
It is suggested for Envoy-S (Line-to-N/G) system. but, Double stage filter has a good filtering on DM signal. Especially, this model shows 60dB insertion loss on DM. so, I have expected, it will filter the signal.
Insertion Loss (dB) = 20 * log10 ( Unfiltered / Filtered)
60dB means, 20 * 3 = 1000/1, the signal should be filtered by 1/1000 at 150kHz
Even consider some decay at 100kHz, the filtering performance should be 1/100 or better.
Leakage current of this filter is 1.8mA, it is pretty high loss
but, envoy is showing ‘Communications from other Envoy(s) have been detected’ early morning. And it is disappearing till evening, and showing again.
I have installed GTX-2300-Y02 between Wire_from_envoy and Breaker_Load_Center
Insersion loss is around 20dB in common mode. there is no differential value.
I am expecting around 10dB minimum, but, the leakage current is 0.5mA,
Too expensive to use it,
Load center and combiner has located as below
MI - Combiner - RP230 - GTX2300 - Critical Load Center - XW 6848 - Main Load Center - Grid
Unfutunately, it can not solve the issue,
the message come again and again ~ like a die hard ....
Wait a minitue, just thinking again,
New Envoy is Line-to-Line communication, so, I have to remove/block a differential mode signal,
it means, the common mode filter is not working.
If install Ferrite Core on L1/L2, yes, it should not working -.-, that is just for old Enovy ONLY. !!!!
GTX-2300, it is a typical single stage common filter, it is good on common noise, and, have some filter for differential mode noise, i feel, that is not strong enough.
and, RP230-30-10, It is double stage filter, it have 60dB insertion loss on DM at 150kHz.
Unfotunately, those filters can not block the signal and, my envoy still detect the other Envoy(s).
BUT, I feel so strange,
(1) it is detected when early morning - when MIs start to work
(2) it is detected when evening - when MIs stop to work
(3) sometime at evening
so, I have tried to check the noise level and filtering level using SA
it makes me so disappointed, because I can not detect any signal from outside for couple of hours.
I have checked my device again, turn-on Enovy and check the signal
My equiment can detect a communication signal which has been generating from my Envoy.
I can find a signal, and confirm the filtering even I can not find the exact level of filtering.
[SO, THERE IS A BASIC QUESTION]
How my Envoy detect the other Envoy(s) signal ?
How my Envoy detect the other Envoy(s) signal after 2 filters ? there is 60dB insertion loss. Is it possible to be detected ?
ANYWAY, most power line filter is designed to minimize the power loss using small capacitor.
It means, not strong enogh on DM filtering, BUT, can not explain the the message while low power mode. Because filter will lost the performance while higher current mode,
I have ordered Q-LCF-064-1P-1 to make sure,
Because it said, IQ compatible,
75W maximum loss (via the maximum current), should be under 1/16 at my appliaction.
anyway, around ~19Wh is so high power consumption
75W x 1/16 & 4.15h = 19Wh per day (or 7.1kWh per year)
Maybe need to try for the DM mode noise
This is showing how cable has connected and where is the panel/inverter has installed on my roof.
This is an simple electric node diagram,
Pretty complex tree than my expectation,
When I have chance, I should clean-up and optimize the wire routing.
becuase I found so many duplicate path, and far routings.
(1) remove cap from top route (between 12-13)
(2) install cap on end of 07
(3) move jumper wire between bottom and middle route, on top - middle
(4) move JB-middle to JB-bottom
and then, Break #1 route will have 9 inverters (longest 6 node)
and, Breaker #2 route will have 6 inverters,
for this job, jumper cable should enought to jump from mid to top.
little doubt ...
2 female connector to make an extension cable
1 connector disassembly clip/jig
Actually, the best method is
(1) make an extra route from bottom to JB
(2) update JB
But, need enough wire clips ...... so many....
The most people charge thier computer or smart phone frequently, and try to keep in full charge status.
They have to understand that is the worst habit to use a lithium chemistry.
When keep the high charge status over long time, battery degradation is happening.
Will lost capacity permanently, this damage can be increased with the temperature of battery (device).
This is why no one recommend do not keep charging all the time, to reduce the average status of charge.
I have 10kWh (51.2V, 200Ah) battery pack already.
But, it is not enough to back-up 2-3 days.
So, I have ordered custom battery pack module (total $6,000 include delivery/bus-bar box).
Each battery pack have 5kWh (51.2V, 100Ah) capacity.
Total 30kWh will enough
2 days without 0 solar production in winter season
3 days with 50% solar production in winter season
unlimited with 100% solar production in winter season
My power usage is around 12~16kWh in winter,
The full solar production is just 10~13kWh in winter, I have to install an extra panels to support full power demand. and planing on this summer
1.4kWAC panel for grid-tie, expected 2~3kWh extra in winter season
0.7kWDC panel for battery back-up, expected 1kWh exra in winter season
Basically, no need to worry in spring/fall/summer, solar panel can generate more than a day amount.
just need a night back-up
Install Schneider XW Pro (6848 Inverter/Charger) for an emergency back-up at home.
I have finished in 2020, but, Just found an installation photo.
I have add 2/3" Plywood on the wall to hold the inverter, it is so heavy (137lb),
And, prepared back-feed to main breaker panel for whole house power.
Inverter / Conduit Box / Gateway / SCP / Extra electric parts (wire / breaker / interlock / conduit / .....),
Total cost is around $5,000