I have requested a detail information abut LCF-064-1P,
Enphase - datasheet only
Manufacturer - can not provide it because customized item
No more solution with LCF, I have decided to return the filter on Enphase,
I am not sure the part is no good, or filtering is not enough.
So, I start to find the solution on my way,
I have reinstalled RP230-30-10-S and GTX-2300
BUT, it has too high line loss, so, I have disassembled & checked GTX-2300.
the coil configuration is the two-in-hand winding, it is good for common mode filtering, But, it has lower magnetic
leakage, so,not good for differential mode filtering. it is not much useful for me.
so, I have removed it. and, reduce 0.5mA leakage current & 10mOhm Resistance Loss
RP230-30-10-S have 60dB 50/50 insertion loss, but, can not block
the signal from next door also, I guess, my noise level at my home is too quiet and no one use PLC devices.
Yes, high SNR, so, just Envoy signal can be detected too easily.
so, I have detected to add an extra differential mode filter using ferrite
Ferrite core is B64290L0082X065
and, look the wire direction, it is the coupled differential mode, and 2 turns.
over one day, it can isolated successfuly, the expected core loss is 200-300Wh per year.
it is much less than 1~2kWh in GTX-2300-Y02.
This configuration will be saturated under 10A. so, I have tried on single turn.
at least, I need 20A because higher current will act as a noise, and will reduce the sensitivity of enovy.
and, I just need this inductor is working at the lower current (quite) zone.
This is final, configuration.
It is working well, now, my system has isolated completely.
and, no more cross-domain-traffic issue.
The cost of Ferrite & RP230 filter is just $80, and under $100 include tax & shipping.
It will working when system current is under 24A (around 20, IQ7+),
If want to apply on the bigger system, need bigger filter